Ace Pelizon Plumbing has provided plumbing services to the residents of Baldwin Park, CA and the surrounding areas since 1957! We’ve seen every plumbing problem you can imagine and we can solve your plumbing problem with ease.
Read our reviews and find out why your neighbors consider us to be their local plumber of choice in Baldwin Park, CA.
for Baldwin Park, CA
Our Reviews by City
Good knowledgeable service
Brian N. - Baldwin Park, CA
A long-time customer.
Brian N. - Baldwin Park, CA
Scheduling is always on time and crews are always courteous.
Response from Ace Pelizon Plumbing:
Thank you Brian. We are happy to hear how pleased you are with the service we provided. I will make sure and let Bryan know how happy you are with everything. We are here for you anytime you need us. Thank you for the opportunity, we look forward to seeing you again when the need arises.
Rita - Baldwin Park, CA
Very professional and up front in explaining the situation!
explaining well the problem
Gabriel - Baldwin Park, CA
Joe Carver He had a lot of patience to explain the root problem
Great service. Dave Robinson and Matt are very professional. I would definitely use this company again for all my plumbing and heating needs.
Silveria - Baldwin Park, CA
Americo - Baldwin Park, CA
On time service, they don't take more time than needed. They fix the problem and they don't left any mess behind.
Diane - Baldwin Park, CA
Gary and Daniel were really nice. They explained everything in detail. The job was completed really fast. Highly recommended.
Good Service, Company doses what they say
Ed - Baldwin Park, CA
Gary was great. Diagnosed problems. gave me options, did he's job quickly, clean and no mess,. Best of all no pressure to buy something I didn't need.
Great and Professional
Tim - Baldwin Park, CA
I believe Gary was his name! He was awesome! He was very knowledgeable and repaired things quickly! He even offered to help clean.
Above and beyond!
Robin - Baldwin Park, CA
I am consistantly and pleasantly surprised by Rob who is always looking to do something better and more efficiently. He isn't about quick and easy which has become more difficult to find in service companies. Thank you!
Mary - Baldwin Park, CA
Everything was done in a very professional manor.
Annual backflow testing and certification 4 devices were tested 4 devices passed
Ace Pelizon Plumbing found a 4 inch clean out in the front yard. Ace Pelizon snaked the mainline and pulled out roots and feminine products. Ace Pelizon camera inspected the mainline and discovered a huge infiltration of roots inside of the mainline about 5 feet in length. There are multiple offsets aud most joints have roots. Ace Pelizon strongly recommends hyrdro jetting the mainline for a temporary fix, or pipe replacement for a permanent solution. The line is draining but further work is necessary. Sewer line at the clean out is 2 and 1/2 feet deep but last good joint is in the street. The sewer line in the sidewalk is 5 feet 8 inches. We can dig it up at the side walk and line to the city main
Ace Pelizon Plumbing was called out on a gas leak. Ace Pelizon Plumbing found that gas line ran from garage water heater to the south exterior wall. The gas run is about 15 ft. Customer was provided the option to initiate a gas leak detection. Approved and we initiated the search for the gas line to go on to the next step. We then confirmed leak was in the ground and the line needed to be replaced. We then dug a 15 foot trench 20 inches deep. We then ran a Polly line from the house to the garage where his water heater is. We installed a shutoff where the line leaves the house. We then pumped air in the line to 10 psi and it held for 10 min. We then laid a tracing wire and caution tape and backfilled. We then put back the existing gas valve and flex line and connected it to the water heater. We left all of the valves off. The customer has called the gas company and they are coming out today.
Ace Pelizon Plumbing arrived at the service location and found water on the carpet in the living room. Ace Pelizon Plumbing then did a leak detection and found leak to be in the slab. We then cut open a hole and jackhammerd the floor to expose the leak on a 1/2 cold water line. We then cut out leaking section of pipe and replaced with type l copper and fittings. We turned water back on and tested for leaks and there are none. We then checked the meter for movement and there is none. We poured a rough patch of concrete. We cleaned area very well and he has Servpro here to do the water restoration.
This toilet is located in the downstairs menâ€™s restroom handicap stall. We will turn water off at the angle stop and replace the Sloan valve. We will then turn water back on and test for leaks.
Arrived at location and found two toilets and one urinal where leaking. One toilet is on the 2nd floor menâ€™s restroom. We rebuilt the sloan valve and got it to stop leaking it is in the handy cap stall . We then went to the menâ€™s restroom on the first floor handicap toilet and tried to rebuild it but there was to much corrosion it would continue to leak. We then went to the menâ€™s urinal in the shop area it is the 3rd one from door and rebuilt that one as well. Everything is working well at this time
Ace Pelizon Plumbing will test and certify 4 back flow devices on site. Ace Pelizon Plumbing will fill out and complete test forms to be submitted to Valley County water district
Annual testing and certification of 1 back flow device Device fail Will submit estimate to rebuild existing device and estimate to replace existing with new back flow device. Ace Pelizon Plumbing will shut water off to backflow device. Will rebuild existing Febco 825y, 1 1/2 inch back flow device, test and certify device at this time.
Possible water leak
Hydro jetting of multi building sewer main line to prevent future stoppages caused by a root intrusion
Leaking shower and install remote controlled toilet seat
Gas main repair
Performed smoke text on 2 story warehouse bulding to find sewer smell
Sink stoppages, snake
Water heater repair at drain valve on older Kenmore water heater
Annual testing and certification of febco 825y backflow device
Drain repair in garage ceiling
Annual testing and certification of a Febco 825Y Backflow device.