Ace Pelizon Plumbing has provided plumbing services to the residents of Fontana, CA and the surrounding areas since 1957! We’ve seen every plumbing problem you can imagine and we can solve your plumbing problem with ease.
Read our reviews and find out why your neighbors consider us to be their local plumber of choice in Fontana, CA.
for Fontana, CA
Our Reviews by City
Great service by Joe the plumber. Ace pelizon is lucky to have Joe Carver working for company. Highly recommend Joe.
Summa sushi - Fontana, CA
Two thumbs up
Response from Ace Pelizon Plumbing:
Thank you so much for your kind words Dave! Joe is truly a gem and we are thankful to have him apart of our Ace Pelizon team. We appreciate the opportunity to assist you with your plumbing needs. We are here for you anytime you need us next.
Ace Pelizon Plumbing tested and certified one backflow device. Ace Pelizon Plumbing will submit paperwork to Fontana Water.
Arrived to test water pressure. Pressure at the backflow device at the water meter is 105 psi, no regulator installed at backflow device or meter. Recommend installation of pressure regulator at backflow device or inspect tenant space to see if there is one installed there that needs replacement. No current access to the tenant space. Returned to check inside tenant space, found 2 inch regulator, tested inside water pressure, over 100 psi, regulator needs to be replaced. Provided estimate, waiting for approval Will check water pressure at backflow device at meter and advise of issues. The service water pressure is very high and all other meters have pressure regulators installed after the backflow device, this device does NOT. Water pressure is over 100 psi. Device serial number 1970056 1-1/2 Meter number 60813461 Returned to site and found a 2 inch pressure regulator in the ceiling space. Checked the water pressure at the mop sink, over 100psi, regulator needs to be replaced. A
Performed walkthrough of facility and took photos of water supply systems. Will review and determine if submeter is possible and prepare pricing for that if so. Walkthrough of facility to determine if submeter installation is possible.